Information Archived on the Web
Information identified as archived on the Web is for reference, research or recordkeeping purposes. It has not been altered or updated after the date of archiving. Web pages that are archived on the Web are not subject to the Government of Canada Web Standards. As per the Communications Policy of the Government of Canada, you can request alternate formats. Please "contact us" to request a format other than those available.
The following are Integrated Mechanical Systems (IMS) that have been tested by a third party accredited by the Standards Council of Canada according to CSA P.10-07 “Performance of Integrated Mechanical Systems for Residential Heating and Ventilation” and meet or exceed the Standard's premium performance requirements. The premium performance target requires that the system achieve a minimum Overall Thermal Performance Factor (OTPF) of 85 percent.
An IMS performs three functions: space heating, domestic hot water heating and heat recovery ventilation. An IMS saves energy by using a sophisticated control system to ensure that excess heat generated by one function is used by the other functions, thereby maximizing energy recovery.
Natural Resources Canada does not endorse the services of any contractor, nor any specific product, and accepts no liability in the selection of materials, products, contractors or performance of workmanship.
|Units||Specific Product Information|
|Manufacturer||N/A||NY Thermal Incorporated (NTI)|
|Fuel Type||-||Natural Gas|
|Space Heating & Water Heating|
|Space Heating Capacity||Watts||27900|
|Composite Space Heating Efficiency||%||89|
|Water Heating Performance Factor||N/A||0.81|
|Nominal burner input||Watts||43950|
|Controls Power (Pcont)||Watts||13|
|Circulation Power (Pcirc)||Watts||103|
|One hour delivery rating (DHW only)||Litres||905|
|One hour delivery rating (concurrent SH load)||Litres||908|
|Airflow rate supply||Litres/sec||34|
|Airflow rate exhaust||Litres/sec||34|
|Rating Condition 1 - Power (fan+preheater)||Watts||54|
|Rating Condition 2 - Power (fan+preheater)||Watts||54|
|Low Temperature Ventilation Reduction||%||83|
|Rating Condition 1 Efficiency||%||60|
If you find inaccuracies or know of any models that should be included on this list (revised November 1, 2012), contact the Office of Energy Efficiency.
If you obtain an evaluation for your property using the EnerGuide Rating System, these units may be eligible for certain regional programs and incentives. For links to lists of other types of energy efficient equipment, consult the Compare Product Models page.
Next: Mobile home furnaces