Energy Efficiency Regulations
Amendment 14 to the Energy Efficiency Regulations was published in Canada Gazette Part II on October 31, 2018. While some provisions come into force upon publication, most provisions of this Amendment will come into force on April 30, 2019. The Guide to the Regulations will be updated with new requirements for affected products in time for the coming-into-force of the Amendment.
Ground-source heat pump, a single package or split-system heat pump that is factory-built, has a cooling or heating capacity of less than 40 kW (135 000 Btu/h) and is intended for application in open- or closed-loop ground-source systems.
Manufactured on or after June 1, 2006
Compliant product models
Ground-source heat pumps as listed on NRCan’s searchable database
Table 10A, 1st row for the open-loop system, if any and Table 10A, 2nd row for the closed-loop system, if any
Energy efficiency regulations by province
Some provinces also have their own energy efficiency regulations for many of the federally regulated products – find out which ones!
Energy efficiency standard
|Product type - Cooling||Minimum efficiency|
|Open systems – no greater than 40 kW with 15°C entering water||4.75 COPc|
|Closed loop – no greater than 40kW with 25°C entering water||3.93 COPc|
|Product type - Heating||Minimum efficiency|
|Open systems – no greater than 40kW with 10°C entering water||3.6 COPh|
|Closed loop – no greater than 40kW with 0°C entering water||3.1 COPh|
COP = Coefficient of performance – a ratio for both the cooling (COPc) and heating (COPh) modes calculated by dividing the capacity expressed in watts by the power input in watts, excluding any supplementary heat
kW = kilowatts
Energy efficiency report requirements
- name of product
- brand name
- model number
- name of the certification body or province whose verification mark will be on the product or its package
- cooling capacity; in kW (Btu/h)
- heating capacity; in kW (Btu/h)
- Air-conditioning and Refrigeration Institute (ARI) classification
- cooling coefficient of performance
- heating coefficient of performance
- whether the heat pump is to be used in a closed-loop or open system, or both a closed-loop and open system
Download the energy efficiency reporting template.
This document does not constitute part of the Energy Efficiency Act (Act) or its associated regulations. This document is an administrative document that is intended to facilitate compliance by the regulated party with the Act and its associated regulations. This document is not intended to provide legal advice regarding the interpretation of the Act or its associated regulations. If a regulated party has questions about their legal obligations or responsibilities under the Act or its associated regulations, they should seek the advice of legal counsel.
- Date Modified: